§ 109.716. Nitrification control plan.
(a) A public water system that uses chloramines or purchases water that contains chloramines shall develop a nitrification control plan by April 29, 2019. The plan must conform to the guidelines in industry standards such as the American Water Works Associations M56 Manual on Nitrification and contain at least the following information:
(1) A system-specific monitoring plan that includes, at a minimum:
(i) The list of parameters that will be monitored such as pH, free ammonia, total chlorine, monochloramine, HPC, nitrite and nitrate.
(ii) The monitoring locations.
(iii) The monitoring schedule.
(2) A response plan with expected water quality ranges and action levels.
(b) The public water system shall implement the nitrification control plan in accordance with accepted practices of the water supply industry.
(c) The public water system shall review and update the plan as necessary.
(d) The plan shall be retained onsite and shall be made available to the Department upon request.
The provisions of this § 109.716 issued under section 4 of the Pennsylvania Safe Drinking Water Act (35 P.S. § 721.4); and section 1920-A of The Administrative Code of 1929 (71 P.S. § 510-20).
The provisions of this § 109.716 adopted April 27, 2018, effective April 28, 2018, 48 Pa.B. 2509.
No part of the information on this site may be reproduced for profit or sold for profit.
This material has been drawn directly from the official Pennsylvania Code full text database. Due to the limitations of HTML or differences in display capabilities of different browsers, this version may differ slightly from the official printed version.