§ 57.81. Hazardous areas.
(a) Boiler or furnace rooms, repair or maintenance rooms, trash rooms, and rooms or spaces used for the storage of combustible materials in quantities deemed hazardous by the Department shall be separated from other areas of the building by 1-hour partitions, floors and ceilings. Openings shall be protected by C label door assemblies. Combustion and ventilation air for boiler, incinerator or heater rooms shall be taken directly from and discharged directly to the outside air.
(b) American Gas Association approved gas fired forced air furnaces and space heaters; U. L. approved electrical resistive coil heating furnaces and U. L. approved oil fired forced air furnaces and space heaters need not be enclosed.
No part of the information on this site may be reproduced for profit or sold for profit.
This material has been drawn directly from the official Pennsylvania Code full text database. Due to the limitations of HTML or differences in display capabilities of different browsers, this version may differ slightly from the official printed version.