CORROSION AND DETERIORATION PREVENTION
§ 245.531. General corrosion and deterioration requirements.
(a) Aboveground storage tank systems must be continuously protected from corrosion and deterioration.
(b) Metallic tank bottoms in direct contact with the soil or other electrolyte shall be evaluated by a corrosion expert to determine if cathodic protection is necessary or appropriate.
(c) Tank bottoms that are not adequately protected from corrosion and deterioration shall be upgraded to meet § § 245.532 and 245.534 (relating to cathodic protection systems; and interior linings and coatings).
The provisions of this § 245.531 amended December 21, 2018, effective December 22, 2018, 48 Pa.B. 7875. Immediately preceding text appears at serial page (384209).
This section cited in 25 Pa. Code § 78a.57 (relating to control, storage and disposal of production fluids); and 25 Pa. Code § 245.521 (relating to performance standards for aboveground storage tanks).
No part of the information on this site may be reproduced for profit or sold for profit.
This material has been drawn directly from the official Pennsylvania Code full text database. Due to the limitations of HTML or differences in display capabilities of different browsers, this version may differ slightly from the official printed version.